Question about Electrical Supplies
On a 230 volt std hook up here's the way it is supposed to work. From black to white you should get 115 volts. From Red to white you shoudl get 115 volts. From red to black you should get 230 volts.
Concentrate on getting the correct output from the generator with the load to the house disconnected
This should be 115v (black to white, 115 volts red to white and 230 volts red to black.
On the load side (ie, the house connected) what are you using? 115 volt lights, etc on one side of the
230 volts, and some other 115 volt loads on the other side.. Are there any 230 volt loads. It could be
that one side of the 230 volts (ie, a 115 volt side is drawing a lot more current than the 2nd 115 volt leg.
Get back with me on just what the loads are botth 115 volt and 230 volt . also what are the rating on the circuit breakers.
Posted on Nov 06, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 07, 2014 | AO Smith A O Smith Motors A O Smith 2hp...
on Sep 23, 2009 | 1998 Ford Explorer
on Sep 09, 2009 | 2004 Dodge Ram 2500
May 27, 2014 | AO Smith 1.5 hp Swimming Pool - Jet / Well...
May 31, 2010 | Plumbing
Jan 18, 2010 | Roper REX4634KQ Electric Dryer
Oct 24, 2009 | Plumbing
Jan 04, 2009 | Estate TEDX640JQ Electric Dryer
Feb 14, 2008 | Dryers
313 people viewed this question
Usually answered in minutes!