Question about Honeywell Heating & Cooling
If you switch the fan to ON does it run the fan?
If so you just proved both the high and low voltagesare there.
does the stat send a signal on W for heat?does that W get passed the saftetys as in flame roll outs limits etc?
does the inducer motor run? if so does the presure switch or centrifigual switch close proving its running?
if so is the ignition working, either hot surface ignition or spek type? WE NEED TO KNOW THIS.
Posted on Feb 25, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 27, 2014 | Goodman Manufacturing Goodman...
Dec 15, 2013 | Carrier 3 Ton 13 Seer Commercial Gas Pack...
Aug 01, 2010 | GE WSM2700D Top Load Stacked Washer /...
Mar 09, 2010 | Heating & Cooling
Nov 04, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 29, 2009 | Maytag Neptune MDG5500AW Gas Dryer
Dec 19, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
37 people viewed this question
Usually answered in minutes!