Question about Goodman GMS90703BXA Heater
Started about a month ago with the central air.the blower would run continuosly and the condenser would cycle like it was supposed to.now that I need to turn on the heat the blower runs but that is it.I've ran thru the schematic and tested all the wires.All the n.c switches are in the n.c. position and the n.o. are all in the n.o. positions.There are five relays on the board but none of them are stuck.(the blower relay I can watch cycle on when power is applied) Am I looking at a bad board or is there something else I can try????
Is it a gas furnace? have you checked your filters? when the blower runs continuosly apon start up most of the time it is a limit tripped. Goodman puts 2 manual reset on the side of the blower motor hard to get at , but 1 may be tripped, i have been on 7 service calls and all the same problem filter plugged and limit tripped.
Posted on Oct 28, 2008
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 04, 2014 | Heating & Cooling
May 25, 2014 | LG LWHD1800R Wall/Window Air Conditioner
Jun 30, 2013 | Heating & Cooling
Sep 22, 2011 | Heating & Cooling
Dec 06, 2010 | Heating & Cooling
Jul 25, 2010 | Intertherm Heating & Cooling
Mar 05, 2010 | Heating & Cooling
Apr 11, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 02, 2008 | Ruud UAMB Air Conditioner
Oct 21, 2008 | Ruud Heating & Cooling
213 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: