Question about Goodman GMS90703BXA Heater
Started about a month ago with the central air.the blower would run continuosly and the condenser would cycle like it was supposed to.now that I need to turn on the heat the blower runs but that is it.I've ran thru the schematic and tested all the wires.All the n.c switches are in the n.c. position and the n.o. are all in the n.o. positions.There are five relays on the board but none of them are stuck.(the blower relay I can watch cycle on when power is applied) Am I looking at a bad board or is there something else I can try????
Is it a gas furnace? have you checked your filters? when the blower runs continuosly apon start up most of the time it is a limit tripped. Goodman puts 2 manual reset on the side of the blower motor hard to get at , but 1 may be tripped, i have been on 7 service calls and all the same problem filter plugged and limit tripped.
Posted on Oct 28, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 24, 2008 | Goodman GMS90703BXA Heater
Mar 01, 2011 | Goodman GMS90703BXA Heater
Dec 30, 2010 | Goodman Heating & Cooling
Nov 22, 2010 | Goodman GDS80904BNA Open Flame Heater
Jan 01, 2010 | Goodman GMS90703BXA Heater
Feb 28, 2009 | Goodman GMS90703BXA Heater
Nov 24, 2008 | Goodman GMS90703BXA Heater
210 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: