Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: We have an LG SQ/SR/ST
i can figure out what model a/c you have from this discription/ is this a lg floor mod. or window model or lg duckless split system
one comon problem causing faut is dirty filter or condensor but hard to figure if i cant place the unit disciption.
Posted on Oct 20, 2008
Error Code: C6 Problem: Inverter compressor run current high
- check [resistance of] compressor windings all equal 1 to 4 ohms
- check [resistance] to earth 50 Mohm minimum
- check run current
I'd also check the motor capacitor(s)
Probably best to explain/print out and give to authorised serviceman
Posted on Jul 16, 2009
Tips for a great answer:
Mar 19, 2016 | LG Heating & Cooling
Dec 31, 2013 | Heating & Cooling
Feb 04, 2011 | LG Heating & Cooling
Jan 24, 2011 | LG Heating & Cooling
Jul 05, 2010 | LG LSC183VMA Split System Air Conditioner
Jul 14, 2009 | LG Heating & Cooling
Jan 31, 2009 | LG Electronic Window Air Conditioner
Oct 20, 2008 | LG Heating & Cooling
460 people viewed this question
Usually answered in minutes!