Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Could be a couple things. First and easiest is to check your intake combustion air supply. If it is blocked by anything or just not enough flow, it will put out the flame. Next would be the flame sensor, usually a temperature probe near the flame front. If it's not reading an increase in temp within a pre-programmed time, it will kill the flame. It can be checked with a multimeter.
Posted on Jan 25, 2008
If the burners do not fully ignite, the sensor will shut the furnace down. The lack of sufficient burner flame is a gas valve or gas pressure problem within the valve.
Replacing the gas valve with the original one may get you going. I surely suggest a professional service company for safety reasons and a thorough inspection. A 20 year old furnace is past it's normal life span.
Posted on Jan 06, 2009
MY FURNACE WOULD RUN FOR ABOUT TWO MINUTES , THEN THE BURNER WOULD GO OUT BUT THE BLOWER WOULD CONTINUE TO RUN , LONG ENOUGH TO COOL THE FAN LIMIT SWITCH DOWN , THEN IT WOULD START THE PROCESS ALL OVER. WHAT FIXED MY PROBLEM WAS THE SECONDARY HEAT EXCHANGER THAT IS LOCATED JUST ABOVE MY BLOWER MOTOR WAS PLUGGED WITH DIRT , WHICH RESTRICTED THE AIR FLOW , CAUSING THE FAN LIMIT SWITCH TO REACH 200 DEGREES AND SHUT THE BURNER DOWN . YOU'LL HAVE TO TAKE THE BLOWER MOTOR OUT TO GET TO IT , BUT MY FURNACE IS RUNNING PERFECT NOW
Posted on Jan 11, 2010
Tips for a great answer:
Dec 12, 2013 | Us Stove Company Vogelzang Norseman Add-On...
Probably your ignitor is bad...
is a tip that will help you try to figure out why your furnace is not
Basic Furnace or Heating System Troubleshooting
Feb 23, 2011 | Mr. Heater Natural Gas Garage Heater -...
Feb 09, 2011 | Sterling RF75 Natural Gas Heater (75,000...
Dec 27, 2010 | Dayton Gas Furnace Heater
Dec 29, 2009 | Dayton Gas Furnace Heater
Nov 17, 2009 | Dayton Gas Furnace Heater
Dec 01, 2008 | Dayton Heating & Cooling
Nov 25, 2008 | Hayward H Series Pool & Spa Heater 400k...
27 people viewed this question
Usually answered in minutes!