Question about Water Heaters
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
not an engineer but maybe a heating compant,, it sounds like you have a relay that has gone bad, you have what we call a winter summer system your domestic water comes from a tank inside the boiler, you might want to think about splitting the system to save you some money in the long run, seperate the water heater from the boiler so you only heat up in the winter, right now you are heating the system that heats your house to get 30 or 40 gals of domestic hot water, it would cost you less by seperating them
Posted on May 30, 2009
This is lack of water flow through the diverter valve.
First have you got a good flow from any cold tap? If yes then see below
If I remember there is a pipe carrying cold mains crossing the lower front of the boiler with an in line filter usually clogged. Remove clean & replace
check also any filter in rising mains to boiler
another cause is the diverter valve itself - diaphram inside may be punctured/split
Posted on Sep 02, 2009
your condensation pipe may be frozen get a hairdryer on it or a hot kettle that should sort it thats the whit pipe on the left usualy plastic
Posted on Jan 09, 2010
Tips for a great answer:
Dec 13, 2013 | Water Heaters
Jun 04, 2013 | Water Heaters
Jan 19, 2013 | Bosch Worcester Spark Electrode...
Jan 11, 2013 | Bosch Worcester Spark Electrode...
Dec 10, 2012 | Water Heaters
Feb 28, 2011 | Water Heaters
Jun 08, 2010 | Water Heaters
Apr 17, 2009 | Water Heaters
Mar 27, 2009 | Water Heaters
37 people viewed this question
Usually answered in minutes!