Question about Jandy Lite 2 Natural Gas Pilot Light Heater
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: heater will not heat
If you dont smell any gas make sure that all gas valves between the heater and the main gas meter are open, and the gas valve in the heater is in the on position. Try cleaning out the nozzles that the gas comes out of. Sometimes they can build up with cobwebs.
Posted on Apr 09, 2009
make sure knob on gas valve(inside heater)is turned to on position.3/4" should be fine as long as heater is not larger than than 175,000 btu
Posted on Aug 11, 2009
I believe you may have a draft restriction and this may stop the start up diagnostics. The draft detection switch is sometimes restricted or weak. Common problem. Tap the gas valve to see if the winter has caused the valve to seat heavily and stick.
Posted on Apr 25, 2010
SOURCE: I have a Jandy Lite
This sounds very much like spider webs in the gas orfaces. If you shut the power off and remove the wires to the gas valve then shut the gas down and remove the fed pipe from the gas valve you should be able to pull the burner tray out of the heater. Now if you remove the burners you should be able to remove the brass orfaces connected to the main gas feed pipe. If you use an air hose or a can of compressed air you can blow this out now. Now take the orfaces you removed and clean them with a tooth pick or a small piece of wire. The webs will look like small cotton balls or lint. They don't stop the gas they just slow it or disperse it and keep it from firing clean and evenly.
At this point you can reassemble the tray and install. This should fix your problem.
Posted on Nov 14, 2010
it is the flame sencor is bad.it is a stick looking tube near the flame. it has one or two wires on it . when it does not sence flame it shuts down.
Posted on Dec 21, 2010
Tips for a great answer:
Jun 07, 2015 | Pool & Spa
May 12, 2013 | Pool & Spa
Apr 10, 2013 | Jandy Laars Lite 2 Pool Heater 250,000 BTU...
Jan 15, 2013 | Jandy Lite 2 Natural Gas Pilot Light...
Nov 29, 2012 | Watches
Jul 02, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Jun 06, 2011 | Teledyne Laars Laars Lite 2 Pool Heater...
Jul 26, 2010 | Kenmore 63942 Dryer
Jun 13, 2010 | Lite On Laars Lite 2 Heaters: 250,000BTU...
Jan 04, 2010 | Mr. Heater Big Buddy Heater
Sep 25, 2012 | Jandy Lite 2 Natural Gas Pilot Light...
138 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: