Question about Generac Electrical Supplies
My new generator had a low battery message. The company that installed the unit replaced a fuse. Now I see a inspect battery message.
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a 10KW SIEMENS
Most of those chargers have a fuse in line between the battery and the charger which you should check. They are two stage chargers meaning when there is a large voltage drop, they go to a high rate charge until battery voltage reads about 14.3 - 14.6 VDC then drops to a float volatge and normal float voltage should be about 13.33 VDC. When they go to a high rate the light turns red, when they go to float the light turns green. When the fuse blows the light stays green because it doesn't see any voltage but the charger isn't doing any work.
Posted on Jul 04, 2011
Tips for a great answer:
Jan 28, 2015 | Generac 12kw Lp/ng Generator With Auto...
Sep 06, 2013 | Generac Guardian 8kw Standby Generator
Sep 10, 2011 | Dometic Rooftop RV Air Conditioner
Jun 23, 2011 | Generac Electrical Supplies
Oct 08, 2010 | Dodge Ram 1500 Cars & Trucks
Sep 08, 2009 | Generac 100 Amp 120/240-Volt Transfer...
Aug 18, 2009 | Electrical Supplies
Sep 14, 2005 | NEC MobilePro 900 Handheld
317 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: