Question about Goodman GDS80904BNA Open Flame Heater
You probably already figured this out, however, more then likely it is the circuit board. It cost aprox $91 (taxes not included) its relativly simple to replace. I had the same issue and that did it for me. Make sure you mark all your connections before removing them and maybe even take a few pictures in case. Good luck!
Posted on Dec 12, 2008
There is a Primary High Limit Switch towards the middle of the furnace, it more than likely needs to be replaced, very common to go out only after a few seasons. Also, you could have a flam rollout switch tripped that will signal the same code, these switches are re-settable and are located on the outer top and sides of the burner assembly, they’re about ½ inch in diameter with a red push button in the center and two wires “ usually purple” coming off of them. If either of these are tripped or bad, the blower will stay on indefinitely.
Hope this helps
Posted on Dec 02, 2008
Tips for a great answer:
Jan 25, 2013 | Heaters
Mar 18, 2010 | Goodman GDS80703ANA Open Flame Mid-Size...
Dec 01, 2009 | Goodman GMS90703BXA Heater
Oct 27, 2009 | Goodman GMS90703BXA Heater
Oct 17, 2009 | Goodman Heaters
Apr 06, 2009 | Goodman GMS90703BXA Heater
Mar 10, 2009 | Goodman GMS90703BXA Heater
146 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: