Question about Goodman GDS80904BNA Open Flame Heater
You probably already figured this out, however, more then likely it is the circuit board. It cost aprox $91 (taxes not included) its relativly simple to replace. I had the same issue and that did it for me. Make sure you mark all your connections before removing them and maybe even take a few pictures in case. Good luck!
Posted on Dec 12, 2008
There is a Primary High Limit Switch towards the middle of the furnace, it more than likely needs to be replaced, very common to go out only after a few seasons. Also, you could have a flam rollout switch tripped that will signal the same code, these switches are re-settable and are located on the outer top and sides of the burner assembly, they’re about ½ inch in diameter with a red push button in the center and two wires “ usually purple” coming off of them. If either of these are tripped or bad, the blower will stay on indefinitely.
Hope this helps
Posted on Dec 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 25, 2013 | Heating & Cooling
Jul 27, 2017 | Goodman Heating & Cooling
Mar 18, 2010 | Goodman GDS80703ANA Open Flame Mid-Size...
Oct 27, 2009 | Goodman GMS90703BXA Heater
Apr 06, 2009 | Goodman GMS90703BXA Heater
Jan 09, 2009 | Heating & Cooling
Nov 25, 2007 | Goodman CLQ36AR49 Air Conditioner
147 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: