Question about Goodman Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Rmove the two screws holding the blower in place and slide it out. With the power off, rotate the wheel and inspect for debris or an impingement. If everything turns easy, you have a bad motor or start capacitor. If you have rubbing, adjust the wheel. If the motor will not turn, replace it.
Posted on May 30, 2008
You need to type GOODMAN GAS APPLIANCES into you browser to find you local servicecenter. I must tell you that Goodman only sells to authorized service companies in my experience. So you become EgKraft Company.
Posted on Nov 07, 2008
You have a limit switch located in the furnace (a little bigger than a dime and located near the center of the front panel, sometimes the switch is mounted to a small fiberglass board) . There will be two wires going to it. They sometimes trip so often that they fail to automatically reset(due to dirty filters or undersized ductwork). You can SHUT OFF POWER TO THE FURNACE, then remove the two screws holding the switch in the furnace, pull the switch out of the furnace and tap on it and wipe it off.
The switch may work a few more times but should be replaced with the same size and type. You will see some rating printed on the switch somewhere. Write down all the numbers and get a replacemet from a furnace/AC supply house. If you have a meter and know how to use it you could check the switch for continuity.
Sometimes just a tap on the switch will get it going. There will also be a couple of rollout switches that could be tripped. They have little buttons on them to reset them. If they trip it may have other issues to be solved.
Hope this helps!
Posted on Feb 01, 2009
In the lower portion of the furnace you'll see where the blower housing is hung in the center of the furnace. There are two bolts you'll need to remove to pull out the whole housing. Depending on the size furnace you have you may have to unmount the control board and set it aside. Don't worry there is no need to remove the wires from the board. Once you have the housing out set it on its side (motor side down) and you'll see a shaft where the blower wheel mounts onto the motor shaft. There should be a bolt you can tighten. first loosen the bolt and put the housing right side up. after that center the wheel on the shaft so that neither of the sides of the wheel are rubbing on the housing once you find that spot where the wheel spins without rubbing tighten that bolt on the shaft and reinstall. should the problem persist you may need to replace the blower housing and/or wheel. I doubt the motor will have to be changed.
Posted on Aug 24, 2009
SOURCE: heater won't heat very long
there isnt a pilot if it has jets , it has a Hot surface ignitor. you should see a glow and then the jets light , if its running for a few min it may be overheating, have you changed the filter recently? you should also have a flash code you can locate when the furnace shut off and is no longer doin what its supposed to look thru the bottom door peep hole and watch for a series of red flashes. if you remove the cover after retrieving the flash code there will be a chart on the inside of the cover that will tell you why the furnace is shutting off. by the way the model # you gave is for the A/C coil above the furnace, not the furnace.
Posted on Oct 10, 2009
Tips for a great answer:
Mar 14, 2014 | Bryant 352AAV036060 352AAV 60,000 BTU, 92%...
Dec 24, 2013 | Goodman GMS90703BXA Heater
May 10, 2017 | Goodman Heating & Cooling
Jan 27, 2011 | Goodman B1859005 Induced Draft Blower...
Dec 27, 2010 | Goodman GMS90703BXA Heater
Dec 23, 2010 | Goodman GMS90703BXA Heater
Jun 16, 2010 | Goodman GMS90703BXA Heater
Dec 29, 2009 | Goodman GMS90703BXA Heater
Nov 03, 2009 | Goodman GMS90703BXA Heater
Aug 15, 2009 | Goodman GMS90703BXA Heater
55 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: