Question about Goodman Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You need to type GOODMAN GAS APPLIANCES into you browser to find you local servicecenter. I must tell you that Goodman only sells to authorized service companies in my experience. So you become EgKraft Company.
Posted on Nov 07, 2008
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the ignitor. The ignitor will glow and you will be able to see it if viewed thru the small inspection port. Once the ignitor gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the ignitor does not energize (bad control, bad ignitor), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not lite (dirty pilot), the burner does not lite (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Most newer furnaces will have a diagnostic center or control built into the control module. You may be able to view it as it is running thru a small viewing port. Some models will require the removal of an access panel prior to finding it. On the reverse of the access panel, there will be a diagnostic chart that will aide you in understanding any error code recorded (usually a blinking light).
Posted on Oct 18, 2009
The sequence of events for furnace operation is -
Fan purge for 30-45 seconds. During this time, a pressure switch is actuated by the running of the purge fan, proving the control board the purge fan is running.
After purge and purge prove, the hot surface ignition and or spark begins. After a few second delay, the gas valve will open. The control board then monitors for flame prove through another sensor located near the burners. If there is no flame within 3-5 seconds, the gas valve closes. It will repeat this process, usually 3 times, before it shuts the system down, which requires a power down of the system to reset.
I have seen trash get into the hose between the purge blower and the purge switch. But you could be having other problems.
Posted on Dec 17, 2009
Tips for a great answer:
Oct 10, 2016 | Goodman Heating & Cooling
Jun 27, 2008 | Goodman Heating & Cooling
Jan 06, 2015 | Goodman Heating & Cooling
Nov 03, 2014 | Goodman Manufacturing Goodman GMH81205DX...
Oct 06, 2012 | Cozy Enclosed Front Console Heater 70,000...
Oct 06, 2012 | Goodman Manufacturing GMH950453BX - 45,000...
Nov 11, 2011 | Goodman GMS90703BXA Heater
May 14, 2010 | Goodman GMS90703BXA Heater
Dec 17, 2009 | Goodman Heating & Cooling
Dec 02, 2009 | Goodman GMS90703BXA Heater
46 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: