Question about Heating & Cooling
My Ruud (upka-024jaz) heat pump will come on then the outside fan stops, but the inside fan runs giving me cool air. I press the high pressure reset and the outside fan starts and gives heat then it shuts off again giving cool air (not AC).
A repairman put a gauge on it and said that it stops at a bit more than 400 and the compressor heats up as well. Its ok in the AC mode.
I am not sure I need a compressor and a pressure switch as he suggested.
YOUR OUTDOOR FAN MOTOR SHOULD NEVER SHUT OFF IN THE AC MODE. IT IS SUPPOSED TO SHUT OFF IN THE HEAT MODE WHEN ITS IN DEFROST. IF THE UNIT IS RUNNING IN COOL AND THE OUTSIDE MOTOR QUITS ,THE COMPRESSOR WILL QUIT SOON AFTER. EITHER THE RUN CAPACITOR FOR THE FAN IS BAD OR THE FAN MOTOR ITSELF IS BAD, IF CAP IS GOOD THEN THE MOTOR IS At FAULT. THE OUTDOOR PRESSURE SWITCH CAN ALSO OPEN IF THE INDOOR FAN MOTOR FAILS IN HEAT OR THE FILTER IS PLUM NASTY in heat OR THE INDOOR COIL IS PLUGGED UP in heat.. THE PRESSURE SWITCH USUALLY TRIPS AT 400 TO 425 SO ITS WORKING CORRECTLY. YOU MAY BE CONFUSING THE ISSUE SAYING THAT THE AIR IS HOT AND COLD INSIDE. IT IS COLD WHEN AC IS RUNNING HOT WHEN HEAT PUMP IS RUNNING IN HEAT BUT ESSENTIALLY not cold or hot if compressor isn't running, but a lot of folks describe the lack of cold air as hot when the compressor isnt running. but it basically is warm or house air temp.you test the capacitor with a capacitor tester or take it to motor shop and let them test it. odds are its a 5 , 7.5 or a 10. it should test within 10 % of rated value . ask for a RESCUE brand replacement motor. they are great ,reversable etc.carefully oil and sand the motor shaft and note exactly where the blade was located in relation to the grill so you get it back just the same. usually they wire up black to a leg of 220 power. white to the other leg of 220 power. brown and brown with white stripe to the capacitor.you can also pull whole fan shroud assembly on some units and take whole thing to motor shop and let them test motor cap, replace and all you do is return to unit and connect two power leads,
Posted on Oct 26, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 20, 2015 | Ruud Heating & Cooling
Jun 25, 2014 | Ruud Central System Air Conditioner
Mar 27, 2011 | Heating & Cooling
Dec 09, 2010 | Ruud Central System Air Conditioner
Jan 17, 2010 | Ruud Matching Split Air Conditioner
May 25, 2009 | Ruud Central System Air Conditioner
Nov 17, 2008 | Ruud Heating & Cooling
Mar 18, 2017 | Heating & Cooling
Mar 15, 2008 | Heating & Cooling
1,055 people viewed this question
Usually answered in minutes!