Question about Siemens 200 Amp Main Breaker 30 Spaces 40 Circuits
I have a 3030. Can I swap out the bus in the existing enclosure to a 3040 bus and use tandems for 4 more circuits? Dont want to remove/replace the can. Planning on killing the main, and swapping bus and breakers. (licenced JW)
While this may appear to be doable - the fact remains that the interior and enclosure are tested, approved and listed by UL / FM / etc. as an entire assembly. Taking from one and replacing with another results in a combination that was not listed.
If however, the enclosures of the two panels are identical - then I suppose I would consider doing the same thing. I would be sure to change out the panel cover so that the cat number and info matches the bus.
Posted on Apr 04, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 04, 2014 | Siemens Electrical Supplies
May 26, 2013 | Square D Co. HOM130C Circuit Breaker
Aug 05, 2012 | Siemens Ite Twin Q1515 Circuit Breaker...
Sep 18, 2011 | Siemens Ite Twin Q1515 Circuit Breaker...
Feb 22, 2011 | Siemens Q1515NC Circuit Breaker Two1Poles...
Sep 10, 2010 | Your One Source Square D #HOME250SPA 50A...
Feb 06, 2010 | HP 100GB Ultra ATA/100 EIDE hard drive -...
Jan 07, 2010 | Siemens /ITE 100Amp 3-pole molded circuit...
Sep 23, 2011 | Siemens 200 Amp Main Breaker 30 Spaces 40...
804 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: