- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
homeappliance.manualsonline.com > ... > Carrier Thermostat Appliance manuals and free pdf instructions. Find the user ... Carrier 33CS450-01 Thermostat User Manual. Page 1 ... Carrier Corporation 04/06. Use with most ...
If the bearings are worn there will be more to just replacing the bearings. The gear mesh pattern has changed so when you replace just the bearings there's a chance there will be an annoying noise coming from the final drive unit that won't go away. It may be necessary to replace the output gears .
Orange or O terminal on Tstat energizes valve in colling cycle. Go to outside unit jumper red to orange and see if Reversing valve energizes. If it does . Problem inside possible Tstat. You shoulf here the valve click. Have someone inside switch from off to cool you should here valve. Rusty
carrier did sell some systems with R407c as a quick fix to gov regulations for about 2 yrs. R407c is a blend . and is treated like R410a except R407c pressures are more simular to R22. being that the pressures run the same the system should work with out changing any parts that being said if the evaporator has been used for R22 the oil residue wiil give you problems ifit is a new unit you would be ok.
not only do you need the nozzles....you will need the spring changed in the gas valve and a manometer to set the proper gas pressure output from the valve.If you change the jets only you could do alot of damage to your furnace.