Question about Heating & Cooling
The motor should spin when the boiler is switched on. One end of the motor spins the fan the other end works the pump. The control box then starts the transformer that starts a spark. The control box then opens up the oil. The boiler should then light if any of the above or the boiler does not light, the boiler will go to lockout.
From what you say the motor is not spinning, thus it could be the motor or more like the pump.
YOU SHOULD NOT PLAY WITHE THE PUMP
If the wrong setting is made it could 1 burn out the back of your boiler 2 go to soot and the boilers in an hour would be filled up and become a fire risk. 3 not start at all if the setting is too low it is a fine line to get it to work and needs the right tools.
Posted on Oct 01, 2009
If the moror just humes then locks out, more that likely the capacitor (small white cylinder like object below control box), get yourself a 5uf capacitor, 2 wires, jobe done!!
Posted on Nov 19, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2017 | Heating & Cooling
Dec 21, 2015 | Ovens
Sep 23, 2013 | Honeywell Biasi B10-3 Boiler ,riello...
Feb 15, 2012 | Heating & Cooling
Feb 02, 2011 | Heating & Cooling
Sep 25, 2010 | Heating & Cooling
Apr 19, 2010 | Heating & Cooling
Apr 06, 2009 | SySTOR Systems (400S52) Burner
Jan 19, 2009 | Heating & Cooling
Dec 27, 2008 | Heating & Cooling
2,084 people viewed this question
Usually answered in minutes!