Question about Honeywell Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
First make sure this is a heater set up for a remote mounted thermostat. If so, the gas valve has 3 screws labeled TH (thermostat) and TP (thermopile) that's the flame sensor with 2 wires coming off it, I don't know where the goofy name comes from. there will be one screw that has both, usually the top one. Wire accordingly. The new valves have a solenoid on the bottom. this connects to the high temp. sensor up top. It has 2 wires on it, one connects to the thermostat wire, the other goes to the screw with TH and TP. Or you can skip it and connect the wire from the back of the valve to the Th and TP screw. Make sure the thermostat wires aren't pinched somewhere, thus eliminating the thermostats control.
Posted on Mar 02, 2008
SOURCE: honeywell thermostat
Hold down the system button on the left side of the screen for a few seconds then after the screen changes hold the two buttons to the left and right of the center button on the bottom of the screen then use the left arrows to get to 670 and the right arrows to get to 0 that is how I unlock mine? Good luck!
Posted on Oct 20, 2008
You need a specific thermostat for a Wall Furnace it is a Millivolt Thermostat and not a 24v standard thermostat....usually it will work anyway however if the powerpile (generator produces millivolts from the pilot light) is weak it may not be producing enough...or the Pilot light may be dirty and lazy...won't produce enough millivolts ...or you can have bad or dirty contacts or connections....or a combination of any of the above.....a 24v Thermostat and particularly a non-mercury thermostat has too much resistance in it for a millivolt system....as your Wall Furnace (other than the fan) runs on less than 1 volt
Posted on Oct 31, 2009
Tips for a great answer:
Dec 25, 2014 | Samsung Refrigerators
Jun 30, 2014 | Kenmore Refrigerators
Nov 12, 2011 | Heating & Cooling
Nov 28, 2010 | Electrolux Dryers
Here is a tip that tells you how to get a manual for most any Honeywell product online...
Manual Honeywell How to Find Honeywell Manuals
Nov 26, 2010 | Honeywell Programmable Thermostat Heater
Feb 22, 2010 | Honeywell Programmable Thermostat Heater
Oct 21, 2009 | Honeywell Programmable Thermostat Heater
Jul 04, 2009 | Frigidaire Gallery Series GLHS269ZDB 36"...
Jan 26, 2009 | 2000 Audi A8
Jan 23, 2009 | Heating & Cooling
131 people viewed this question
Usually answered in minutes!