Question about Dayton Heating & Cooling
I need 3VE51A manual.
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Here is a link to your owner's manual... http://188.8.131.52/manuals/123919-01A.PDF. Look on page 8 and 10. It could be several things. It could only be a dirty fuel filter or the pump pressure may just need adjustment. If you need a part you can contact Master Parts at 800-466-1446 or you can find them on-line at www.masterparts.net. I hope this helps!
Posted on Jun 30, 2009
I would cotact Grainger industrials supplies by callig 1-800-323-0620. Or e-mail at Grainger.com I have dealt with this company for 25 years and I've always been happy to do business with them. Hope this helps you. You will need name brand,part description,and part no. if possible.
Posted on Nov 18, 2010
Just repaired one of these, problem was that main gas valve was not opening, valve is controlled by a vacuum switch, vacuum is created as fan blows air down tube past bent up metal flap near front bottom of heater (slight low pressure zone created). If vacuum switch is miss adjusted it will not close when fan is running and no gas flows. this is easy to check as vacuum switch also has a pressure port on it. With gas disconnected, remove bottom cover, locate vacuum switch (it has a hose clear plastic hose connected to it, in opposite corner is another hose connection, attach a length of hose to it that you can blow lightly into. With heater plugged in and no gas connected (USE CAUTION OF WIRE!!!), turn heater on you should hear after a few seconds the ignition and then a loud click as the gas valve opens, if no click blow lightly into end of your added tube, if you now hear a click the gas valve just opened. if you stop blowing you might hear the gas valve click again as it re-closes. If this is the case the vacuum switch needs to be adjusted slightly. THIS switch is hear for your safety, Adjust at your own risk!!! This can be done with a screw drive in the top, rotate screw slightly while checking if the fan alone causes enough vacuum to make the switch work. DO NOT over adjust. check safety operation before hooking up gas by placing a piece of cardboard or wood over the air intake and the exhaust to block airflow, if the air flow is blocked you should hear the gas valve drop out and reconnect as air flow is reestablished. Hope this helps
Posted on Feb 13, 2011
Tips for a great answer:
Jan 09, 2016 | Dayton Electric Heater
Dec 21, 2015 | Dayton Heating & Cooling
Jan 05, 2014 | Water Heaters
Jan 08, 2012 | Dayton Heating & Cooling
Dec 08, 2011 | Dayton E50 Heater
24 hrs / 365 days a year
2E510F, 2E511F, 3E218E, 3E219E
Please provide following information:
-Serial number (if any)
-Part description and number as shown in parts list
102548-03 (part you need)
Thanks for choosing FixYa,
Nov 19, 2010 | Dayton Heating & Cooling
Nov 18, 2010 | Dayton E48 Oil Filled Utility Heater
Nov 30, 2009 | Dayton E50 Heater
May 04, 2009 | Reddy Heater-170,000 BTU Kerosene Deluxe
Jan 30, 2009 | Dayton E48 Oil Filled Utility Heater
Apr 16, 2018 | Dayton Heating & Cooling
185 people viewed this question
Usually answered in minutes!