Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Air Conditioner malfunction
Hi, Sounds like you have a short in the control circuit to me. Turn off all power going to the unit. Write down or otherwise mark the wires leaving the control board going to the thermostat. Remove them from the control board. Replace the fuse. Turn power back on and see if the fan still runs. If it does, check and or replace the heat limit switch that brings the fan on during the heat cycle. It may just need adjusted. If the fuse blows, I would think that the control board is probably bad. If it doesn't blow, Remove the thermostat. Leaving all thermostat wires open check them with an Ohm meter. There should be no continuity between them. Twist all the wires together at one end and ohm them again at the other end. You should have complete continuity on all wires. If the wiring checks out, down power the unit. Double check your wire colors and rewire the control board. With all wires open at the thermostat, turn the power back on. Touch the RED wire to the YELLOW wire. The Condensing unit should come on. Touch the RED wire to the GREEN wire. The fan should come on. Touch the RED wire to the WHITE wire. The heat should come on. Down power the unit. Replace the thermostat. Test unit. If the fuse has lasted ok but blows now it is either wired wrong at the Thermostat or the thermostat is bad. I hope I have helped. NOTE: If you can not understand these instructions. Call a licensed Heating / Air conditioning company. kstfas
Posted on Sep 23, 2007
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
SOURCE: Dometic Duo-Therm - 13,500 B.T.U. Model #3107541.009 - Serial # WA346967 - Yr. 1999-2000. Blower motor will not start. Replaced the start capacitor - no help. It will run by spinning the motor by hand
Yes you should try replacing the run capacitor.
Posted on May 08, 2009
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Dec 21, 2014 | Fasco Intercity Heil / Tempstar Furnace...
Nov 13, 2014 | Heating & Cooling
Oct 17, 2013 | Carrier Icp Heil Tempstar Furnace Blower...
Nov 17, 2011 | Goodman Heating & Cooling
Jul 06, 2011 | Heating & Cooling
Dec 11, 2010 | Honeywell L4064B2236 Fan/Limit Control...
Feb 19, 2009 | Aprilaire 550 Humidifier
May 21, 2018 | Electrolux Heating & Cooling
105 people viewed this question
Usually answered in minutes!