Question about Intertherm P3RA-036K Air Conditioner
This is an iutside unit. I have looked inside the Mobile Home and can not even locate anything but the Floor Vents and the Air Return Vent. I have a Filter in there but there shoiuld be one on the Unit, right? I bought this place used and there are no Owners Manuals. The Lady I bought it from was the 2nd owner and she bought it in 2005 and said she never changed anything except the Floor Air Return Filter. My Electric Bill is way high so I think there may be a problem. Anyone out there have any idea where this Filter may be locaterd? I looked all around the unit and all Panels seem to be permanent.
NO FILTER IN A PACKAGE UNIT EVER AT ALL AT ANY TIME. YOUR FLOOR GRILL FOR RETURN AIRT IS ALWAYS YOUR ONE AND ONLY FILTER LOCATION. YOU MAY HAVE A VERY DIRTY EVAPORATOR COIL ON THE INTAKE SIDE WHICH WOULD CAUSE POOR PERFORMANCE AND POOR AIRFLOW. HAVE AN AC CO COME OUT AND REMOVE THE LID AND INSPECT OR WASH THE COIL. YOU MAY ALSO BE LOW ON R22 . HAVE IT CHECKED WITH A GAGE. AS A GENERAL RULE PRESS LESS THAN 40 POUNDS EQUAL LOW CHARGE OR DIRTY COIL. 65 TO 70 POUNDS FAIRLY NORMAL. IT NEEDS TO BE 70 TO 80 DERGEES OUTSIDE AND INSIDE TO REFLECT THESE GENERAL PRESSURES. IF LOW ON R22 THEN A LEAK HAS DEVELOPED, USUALLY IN THE EVAP COIL.. BE AWARE R22 IS OUT OF PRODUCTION NEXT YEAR. STRONGLY CONSIDER NEW 410 REF UNIT BEFOR ESINKING A BIG CHUNK OF MONEY IN R22 EQUIP
Posted on Oct 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 06, 2016 | Intertherm P3RA-036K Air Conditioner
Aug 09, 2011 | Intertherm P3RA-036K Air Conditioner
Dec 13, 2010 | Intertherm P3RA-036K Air Conditioner
Sep 21, 2010 | Intertherm P3RA-036K Air Conditioner
Aug 09, 2010 | Intertherm P3RA-036K Air Conditioner
Feb 19, 2010 | Intertherm P3RA-036K Air Conditioner
Sep 23, 2009 | Intertherm P3RA-036K Air Conditioner
Jul 12, 2009 | Intertherm P3RA-048K Air Conditioner
Jul 24, 2008 | Intertherm P3RA-036K Air Conditioner
145 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: