Question about Coleman Heating & Cooling
YOUR FAN ON SETTING IS THE SECOND SETTING ON THE SWITCH .THE LOWEST SETTING IS THE TEMP AT WHICH THE FAN CUTS OFF AT THE END OF A SUCCESSFUL HEAT CYCLE. THE THIRD SETTING IS THE TEMP AT WHICH THE FAN COMES ON MAYBE 140 ISH. THE THIRD SETTING IS THE TEMP AT WHICH THE BURNER IS SHUT DOWN IN AN OVER TEMP SITUATION SAY 200 . THEN CONSIDER THE FACT THE SETTINGS ON THE DIAL ARE VAGUE. ACTUAL TEMPS MAY BE 20 DEGREES DIFFERENT, AND PROPERLY SETTING IS USUALLLY DONE WITH AN ELECTRIC THERMOMETOR.
Posted on Oct 25, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 06, 2014 | Intertherm 56000 Btu Gas Furnace
Nov 25, 2010 | Heating & Cooling
Nov 22, 2010 | Goodman GDS80904BNA Open Flame Heater
Dec 04, 2009 | Refrigerators
Nov 21, 2009 | Dayton Electric Heater
Aug 03, 2009 | Heating & Cooling
Feb 14, 2009 | Kitchen Ranges
Oct 20, 2008 | Heating & Cooling
Dec 10, 2017 | Coleman Heating & Cooling
45 people viewed this question
Usually answered in minutes!