Question about LG Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
SOURCE: LG B30AWY fault code ch
Outdoor unit PCB EEPROM failure, try removing EEPROM and refitting if removable (possible contact fault), otherwise replace PCB if the EEPROM is non removable.
Posted on Feb 07, 2011
SOURCE: Air conditioner is turning on
Plesae visit the link provided below :
Posted on May 01, 2011
Tips for a great answer:
Apr 24, 2011 | LG LS-L1210CL Mini Split Air Conditioner
Feb 07, 2011 | LG Heating & Cooling
Jan 02, 2011 | LG Heating & Cooling
Dec 18, 2010 | LG LS-L1210CL Mini Split Air Conditioner
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Oct 13, 2010 | LG Heating & Cooling
Mar 16, 2010 | LG Heating & Cooling
32 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: