- If you need clarification, ask it in the comment box above.
- Better answers use proper spelling and grammar.
- Provide details, support with references or personal experience.
Tell us some more! Your answer needs to include more details to help people.You can't post answers that contain an email address.Please enter a valid email address.The email address entered is already associated to an account.Login to postPlease use English characters only.
Tip: The max point reward for answering a question is 15.
Thanks for your replies, I had a Sharp authorised tech look at it and im told it's the indoor circuit board. Im told its a $360 repair job all up, that sure beats replacing the entire ac or putting up with the heat...
I have same problem like yours to my newly installed Fujitsu multi-split system (the first time use since system installed 1 week ago). I rang the electrician who did the installation; he said it must be the units themselves nothing to do with electricity.
Okay, then I rang Fujitsu and their local service agent. They suggested me to switch off C/B for an hour to reset the units. I followed the instruction but the indoor units still did not respond to remote control...
It simply looks like no power supply to indoor units (they are hard-wired to the outdoor unit). So I used a multi-meter to test the power terminals of indoor units (Danger! If you have no idea about this, don't even try! ): it seemed no power supply even C/B is on. I turned to the isolator which next to the outdoor unit. The isolator was making arcing noise when I switched it on and off. The indoor units suddenly turned on for few minutes then died again.
So I figured out the problem is that crooked isolator. I called the unhappy electrician to replace the isolator. End story....
Hi I have Mitsubishi split unit which is 5 years old. when turn heat mode for 30 deg C on the remote condesing unit runs for about 6 minuts and stops. what would be the Technical problem ?Thanks an Apprentice.
The flashes are codes for different problems the unit may have, count the flashes and check your owners manual this will tell you the problem and the solution, or turn the breaker off for 5 minutes and re-start the unit this will reset it the unit should work if the problem start again you will need a service man. hope I was able to help you.
The flashing light is a delay timer, usually activated when changing from heating to cooling and visa versa. The fact that the unit can only run from certain times shows that the timer is activated. You need to cancel the timer function on the remote.
TOYO mini split air conditioner made in Japan is very very good quality and it can runs for 20 years without any problem. You didn't hire a best ac technician to install your TOYO unit. The tubing connection between indoor unit and outdoor unit is not the right torque and refrigerant leak. Your TOYO unit runs out of refrigerant. You need fix the leak and fully charge the system. You will solve the problem.
TOYO mini split air conditioner made in Japan is very very good quality and it can runs for 20 years without any problem. You didn't hire a best ac technician to install your TOYO unit. The tubing connection between indoor unit and outdoor unit is not the right torque and refrigerant leak. Your TOYO unit runs out of refrigerant. You need fix the leak and fully charge the system. You will solve the problem. Good luck!