Question about Ruud UBHC Air Conditioner
Old Rudd unit works fine but when I cleaned up for the winter heater find the fan will not come on when set on auto. The burner unit fires up but after burning for short period goes out when time for blower fan to come on. Works ok when fan set for ON. Works fine when in AC mode.
The fan is controlled by a fan center or a stack switch. as burners light and heat up the spring sensor on the bulkhead above burners heats up and turns and a a point energizes the indoor fan if it gets to hot the burners go out on safty. sounds like a fan control is bad tap on them gently and they sometimes break loose but if not then have a pro replace fan control and test heat exchanger.
Posted on Oct 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 12, 2016 | Heating & Cooling
Nov 01, 2015 | Heating & Cooling
Oct 12, 2014 | Heating & Cooling
Jun 07, 2011 | Heating & Cooling
Dec 19, 2010 | Heating & Cooling
Oct 17, 2009 | Intertherm P3RA-048K Air Conditioner
Jul 26, 2009 | Heating & Cooling
Apr 07, 2009 | Heating & Cooling
Jan 17, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 03, 2009 | Goodman GMS90703BXA Heater
224 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: