Question about Empire DV-35 Heater
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
It sounds like the gas valve is dropping out. Make sure the system is venting the exhaust(no restrictions). Then make sure all your wiring connections in the unit are tight. In a millivolt system if all wiring connections aren't tight and clean your circuit will drop in millivolts and the gas valve will drop out. The gas valve requires a certain millivolt to stay open. I hope I was of some assistance!! Good luck!!
Posted on Nov 29, 2009
SOURCE: I have a Empire DV210
The pilot ofifice probably has a bit of dirt in it...to get it out you will need to take the pilot apart and clean it out...this can be fairly difficult on those heaters and getting it back together can be a pain...pay attention as you take it apart...blow our the tip with canned air like you would use to clean your keyboard...
Sometimes the "hood" or the cover over the flame will bend up over time and you will also have to bend it down a bit to get the pilot flame onto the thermocouple...make sure the thermocouple is also pushed all the way up in the holder...
Posted on Mar 18, 2011
Tips for a great answer:
Oct 20, 2017 | Heating & Cooling
Jan 01, 2017 | Empire Heating & Cooling
Nov 01, 2013 | Heating & Cooling
Nov 15, 2012 | Pool & Spa
Oct 30, 2011 | Empire DV-35 Heater
Apr 19, 2011 | Empire DV-35 Heater
Mar 18, 2011 | Empire DV-215 Direct Vent Natural Gas...
Feb 04, 2011 | Empire GWT-50 Wall Mounted Panel Heater
Feb 01, 2010 | Empire Heating & Cooling
Nov 02, 2008 | Empire DV-215 Direct Vent Natural Gas...
129 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: