Question about Heating & Cooling
Recovery has nothing to do with on off on off. you have a new digital stat that holds an exact to the degree temp a change of a half a degree can bring it on.. so stat needs to be above main return 5 feet off floor. away from any drafts , doors supplys etc. also be sure the hole in the wall is sealed . the cold air in the wall is more than enough to make stat come on . they are incredibly sensitive.an old mercury bulb stat would have a swin g of 3 or 4 degrees . so set at 75 it may heat up to 78 and stay off till temp fell to 73 so you get a longer run cycle or and longer off cycle. the new ones are on off on off keeping a perfect temp 75 exactly. thory is the heat exchanger is already hot and a quick short cycle is more efficient than being off 20 minutes and reheating the heatexchanger from scratch again. having said that if you look aT the installer set up instructions that came with the stat it may give you an option to reset or adjust the stat so it will have a one (default) two, or three degree adjustment , so 75 equals up or down three degrees on call for heat.see honeywell toll free number in their literature
Posted on Oct 24, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 02, 2015 | Honeywell RTH6350D1000 5/2Day Prog...
Oct 06, 2014 | Honeywell Heat/Cool Thermostat
Dec 16, 2013 | Goodman Heating & Cooling
Mar 11, 2011 | Honeywell CT87B ROUND HEATING&COOLING...
Feb 26, 2010 | Honeywell Programmable Thermostat Heater
Jan 18, 2010 | Honeywell Programmable Thermostat Heater
Mar 25, 2009 | Honeywell Electronic Programmable...
Jan 15, 2009 | Honeywell Electronic Programmable...
Dec 21, 2008 | Honeywell Programmable Thermostat Heater
Nov 15, 2007 | Honeywell Programmable Thermostat Heater
5,847 people viewed this question
Usually answered in minutes!