Question about Honeywell Electronic Programmable Heat/Cool Thermostat - CT3300A100 Heater
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like a relay sticking. Possibly in the thermostat or possibly the furnace relay at the furnace. The next time it happens, unplug the thermostat from the wall. If the furnace still runs then it's the furnace relay.
Hope that helps...
Posted on Mar 07, 2008
Honeywell has a great newer thermostat.
This is what I sell, it is easy to program and use and has a large touch screen. I hooked up 4 in a office and it saved them 15 % of heating bills
http://customer.honeywell.com/honeywell/ProductInfo.aspx/TH8110U1003 this is the link for Honeywell thermostat for the page.
Posted on Nov 30, 2008
Yes you can change that by change the number of cycles per hour that your t-stat looks from for youe furnace. Lower the cycles per hour number and it will increase the range.
You can see how to do it here
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 12, 2009
Good Morning, and yes you said it. Anytime a stat doesn't come on when it is set for a call for heat or cooling, the sensor on the subbase of the stat has lost its ability to sense the correct temperature. I have seen mechanical stats last as long as 25 plus years, but that's truly amazing for a digital stat to last that long. Yes, replace the thermostat. I don't know what kind of system you have, but if its a gas furnace with an a/c, the wiring will look like this. You will have terminals marked R, Red, for the 24 volt hot wire, G, Green, Y, Yellow, and W, White for heat. Going back to the red wire, it should have RC and RH on it. There will be a normally red wire connecting the 2 terminals.The Red wire coming in can connect to either one, as they are all together. The new stat will come with the new Red jumper wire attached. So, if you do have a gas heater, this is very easy to install. The only terminals you will need to use are RH to RC for the incoming red, Y, G, and W for heat. Y is for cool, and G is for fan. Very easy. Now if you have a heat-pump, they have many more terminals and can be a problem wiring them. If you have gas, forget the heat pump. I wont confuse you by going there. If it is a heat-pump, contact me in the comment box to let me know, and I can help you there also. Get a new stat at Home Depot, Lowe's Hardware, or O.S. Hardware. You want a 5 day, 2 day programmable Heating and cooling thermostat, 24 volts.It will have everything you need. See if it takes batteries for the display, they may not come with those, it will say on the box. Turn off your power to heater, so you won't short out the new one.They come in 2 sections, first the stat that just snaps on, and the subbase that is screwed to the wall. It will have the wiring terminals on it. Remove a couple of screws and loosen wires and remove. Be sure you write down how the wires go in case they used different colors, you never know. You will be all set. Store the manual in a safe place for future use. I wish you the best.
A/C, Heating, & Refrigeration Contractor.
PS, Please rate me on this :))
Happy Holidays to you and family!
Posted on Nov 23, 2010
Testimonial: "I hate spending money needlessly replacing items that may not be the problem. Thank you for confirming my suspicions."
Tips for a great answer:
Dec 28, 2016 | Heating & Cooling
Feb 09, 2015 | Heating & Cooling
Aug 29, 2014 | Honeywell Programmable Thermostat Heater
Jan 23, 2014 | Heating & Cooling
Dec 23, 2013 | Honeywell Programmable Thermostat Heater
Dec 08, 2013 | Honeywell Programmable Thermostat Heater
Apr 17, 2013 | Heating & Cooling
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Nov 12, 2008 | Honeywell Programmable Thermostat Heater
Mar 07, 2008 | Honeywell Programmable Thermostat Heater
48 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: