Question about APC Back-UPS RS Battery Backup (apw br1500) UPS System
On the heatsink thats in front the fans theres six fet irfb23n20d mine had the outer two towards the fan short circuited.replaced them and all is well now.
Posted on Mar 14, 2009
I am facing same problem, waiting for solution, searched all APC documents and found out nothing at all. although i guess it is he relay that is faulty
Posted on Dec 19, 2008
a 6ya Technician can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Technician (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 04, 2012 | APC Back-UPS RS BR1500-IN (BR1500-IN) UPS...
Sep 09, 2011 | APC Back-UPS RS BR1500-IN (BR1500-IN) UPS...
Apr 19, 2011 | APC Back-UPS RS Battery Backup (apw...
Sep 18, 2009 | APC Back-UPS RS Battery Backup (apw...
1,007 people viewed this question
Usually answered in minutes!