Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Water level float switch error
You do not mention the model, I presume that it is a cassette, in which case the float switch is located in the indoor unit. You have to remove the cover which is 4 screws. First make sure all power supply is turned off. Then remove the drain pan which surrounds the fan blade. You will see in one corner of the unit a slightly deeper part of the drainpan, this is the corner where both the condensate pump as well as float switch is located. Before you do any of this, give a serious blow into the drain pipe from outside and this may dislodge any sludge which may be causing the floatswitch to stick. You can also pull out a rubber plug which is under the pump on the drainpan.
Posted on Mar 05, 2009
CH-06 REFERS Indoor unit coil sensor fault. Disconnect from PCB measure resistance. 10 kOhm at 10C and 4 kOhm at 30C. if not replace sensor. THANKS.
Posted on Dec 13, 2010
Tips for a great answer:
Dec 05, 2015 | Heating & Cooling
Nov 25, 2015 | Heating & Cooling
Jan 12, 2014 | Haier 539490003 Air Conditioner
Aug 01, 2013 | Heating & Cooling
Dec 13, 2010 | LG Art Cool LA121HNP Split System Air...
Nov 29, 2009 | LG Heating & Cooling
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
Dec 11, 2017 | Heating & Cooling
70 people viewed this question
Usually answered in minutes!