Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Changing Thermostats
This is one where you will need a good control man or woman. The American Standard ASYST system is not intended for the homeowner to change out. It has a room sensor wire that others do not account for.
Posted on Jan 16, 2008
I don't know if this will be helpful or not, but I just installed a new Honeywell and the Honeywell customer service guy helped me get the wires done correctly. The number is 800-468-1502.
Posted on Jan 05, 2009
What was the old thermostat labels and the wire colors that went to them?
The typical heatpump wiring Terminals are:
R = Red = Hot side of Transformer
C-B-X = Common side of transformer Depending on brand of heatpump
Y = Yellow = Cooling Contactor
G = Green = Furnace Blower
O = Orange Reversing Valve Energize to Cool
B = Blue Reversing Energise to Heat Depending on brand of heatpump.
W2 = White = Auxiliary Heat
You need to be sure where each wire comes from when you connect them to the new thermostat.
The best way to do that is to go to the furnace and see where they are connected. R-Y-G are probably correct, you need to see where the Blue wire comes from and determine what the X terminal was on the old thermostat.
Posted on Dec 29, 2009
Tips for a great answer:
May 08, 2018 | Honeywell Heating & Cooling
Nov 29, 2013 | Rheem 3.5 Ton 14 Seer / Ruud 100K Btu 80%...
Oct 23, 2013 | Honeywell TH6220D1028 FocusPRO 6000 5-1-1...
Jan 05, 2011 | Heating & Cooling
Mar 04, 2010 | Heating & Cooling
Dec 15, 2009 | Honeywell Programmable Thermostat Heater
May 16, 2009 | Heating & Cooling
Jan 05, 2009 | Honeywell Programmable Thermostat Heater
Sep 04, 2008 | Honeywell Heating & Cooling
May 17, 2008 | Honeywell Heating & Cooling
195 people viewed this question
Usually answered in minutes!