Question about Ruud Heating & Cooling
Ruud 90+ Model UGRA 10EZAJS is started up in the the morning by setting the tstat to 66 F (actual room temp 59-60 F). Furnace starts and runs fine for a long time (30-40 minutes) as the home temperature climbs to about 63 F - 64F. Then the furnace goes through what appears to be a reset where the flame drops out, the air circulates for a few minutes then the flame tries to come back on. The gas valve cycles open/closed several times but only a partial flame comes up. After several tries the furnace goes into safety lockout and will stay down for 30 minutes. Then the furnace restarts and runs fine the rest of the day. The problem only appears in the morning at first startup. I thought it might be an overtemperature issue. I checked airflow and it is at around 1500 SCFM. Gas (propane) pressure is good. Flame sensor was replaced, gas valve is new. Orefices and gas distribution tubes are clean. Pressure diaphragm switches are new. Furnace filter is clean.
Check for condensation buildup in the Induction Blower housing. The condensate tubes or canister may be blocked and causing the diaphragm switch to trip the unit out causing the burners to shut down.
Posted on Nov 09, 2012
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 10, 2015 | Kitchen Ranges
Sep 11, 2014 | Heating & Cooling
Jan 28, 2013 | Heating & Cooling
Apr 07, 2017 | Ruud Matching Split Air Conditioner
Nov 24, 2009 | Heating & Cooling
Aug 10, 2009 | Heating & Cooling
Jun 24, 2009 | Honeywell Programmable Thermostat Heater
Apr 27, 2009 | Ruud UBHC Air Conditioner
Nov 20, 2007 | Ruud Central System Air Conditioner
727 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: