Question about Honeywell Air Conditioners
SOURCE: I have a coleman evcon
The most common wiring is: This sometimes varies as to installers preferance.
Red wire is your supply power to the T-stat. R terminal
Green wire is the blower fan. G terminal
Yellow wire is compressor contactor Y terminal
older units used a blue wire to Y
White wire is heat auxilary or black wire W terminal
Orange wire is reversing valve O terminal
Blue wire is the common C terminal
Black wire can be emergency heat E terminal
Best thing to do is replace wire for wire from t-stat to t-stat
or write down the colors to which terminal on the old t-stat and match to the new. make sure you SECURE POWER to the Air Handler, furnace and condenser before replacing any t-stat.
It is very easy to short the wires out if the power is left on and take out your A/H low voltage fuse or transformer.
Posted on May 18, 2008
do a s plan plus and buy a poly plumb roomstat combined programer with built in relays as you require the relays to stop back feed! simple!
Posted on Jul 23, 2008
I would say high if you need cooling. If the tempature is cool enough for you then set it to low.If you are hot and need more cooling then high.
Posted on Apr 07, 2009
Hello,You forgot to wire the O terminal w1 witch is the reversing valve.It is important to check if old stat is using O or B in witch case B terminal=w1 leaving O unused.
Posted on Apr 21, 2010
Tips for a great answer:
Oct 20, 2013 | Haier 2.0 Ton Multi-position Air Handler...
Jan 14, 2011 | Air Conditioners
Dec 22, 2010 | Air Conditioners
Jul 03, 2009 | Intertherm P3RA-048K Air Conditioner
Apr 05, 2009 | Honeywell Air Conditioners
Nov 06, 2008 | Air Conditioners
Sep 03, 2008 | Air Conditioners
Jul 19, 2008 | Air Conditioners
382 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: