Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I think I've done it - but don't take this as absolute truth.
For the Honeywell T6360B the original Potterton wiring should be rewired as follows:
Brown [Live] goes to terminal 1; Blue [neutral] goes to Terminal 2 and the yellow/green [which is not an earth but a switched live - i.e. gives live to the heating system when the thermostat clicks in] goes to terminal 3.
Obviously all done with the power isolated and when it was switched back on we had heating again :o)
It's been on over two hours now and all seems fine.
Posted on Feb 16, 2008
I connected the blue wire to the R and the white wire to the W on the old thermostat and shoved the new Honeywell 5-1-1 Day programmable thermostat up the first guys *** that i ran into at Canadian Tire
Thanks for your help
Posted on Dec 29, 2008
SOURCE: honeywell thermostat
I had the same problem and decided to take a chance and call honeywell customer support. I am shocked, they solved my problem! At least in my situation we found that the blue wire ran the compressor. Instead of hooking up to "blue" on the thermostat, we hooked it up to "white." It works wonderfully now.
Posted on Apr 25, 2009
it all depends how things are wired inside your furnace downstairs on a basic system blue is usually a common - C and yellow is for cool - Y just leave the jumper in from R & RC R is 24v power and RC is 24v power in Cool yuo will just have to squeeze the new wire in with it before you get to far i would open up the doors on you furnace and see where the connections are in there so you dont blow any fuses
Posted on Jun 28, 2009
red goes to RC and RH, White goes to W, Green goes to G and Blue goes to Y. iam assuming on the old tstat that Red whent to R White went to W Green went to G and Blue went to Y
Posted on Sep 20, 2009
Testimonial: "Thanks! Worked out great!"
Tips for a great answer:
Sep 26, 2017 | Honeywell Heating & Cooling
Mar 16, 2017 | Honeywell Electrical Supplies
Nov 29, 2011 | Honeywell Programmable Thermostat Heater
Dec 08, 2010 | Honeywell Electronic Programmable...
Jun 26, 2010 | Honeywell Programmable Thermostat Heater
Mar 23, 2010 | Heating & Cooling
Jan 23, 2010 | Honeywell Focus 6300B 5-2 Days...
Aug 12, 2008 | Honeywell Heating & Cooling
720 people viewed this question
Usually answered in minutes!