Question about Leviton MFG L00-IPI06-1LM DIMMER SLIDE CONTROL
The two switches in the question work independently of each other but share the source of power coming into the box.
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You are correct in assuming green is the ground and connects to bare copper wire. Black is always the HOT wire and should be attached to the black wire. Red wire connects to white wire.
Posted on Sep 13, 2009
There are a possible two problems you might have. First a quick explanation of 3-way systems. If you have a common 3-way system, one switch box will have the "Power End" and the other switch box will have a "Switch Leg" end (the wire that goes to the actual light fixture. Then inbetween the two boxes there will be two (usually red / black ) "travelers" that connect to the switch. http://www.electrical-res.com/EX/10-19-02/3-way-switch-wiring-diagram.jpg Here is a link to a standard 3-way system. In the picture, the switch on the left is the "power end" and the switch on the right is the "switch leg" end. the first thing to do is establish whether you are in the "power" or "switchleg" box. You can do this by completely disconnecting the dimmer, then test which wire has power using a voltage meter. (do not use a "hot stick"! the tester that beeps or lights up when it senses voltage. These can give you a false reading) Once you know which wire has power, go to the other switch and flip it. If the same wire still has power, then you are in the "Power" side of the 3-way, IF A DIFFERENT WIRE HAS POWER NOW, YOU ARE AT THE "SWITCH LEG" side of the 3-way. The most frequent mistake made while installing a 3-way switch is getting the common and travelers mixed up. If you are in the "Power end", the "common" (or connection to your dimmers black wire) should be the wire that had power no matter which position the other switch is in. If you are in the "switchleg" box, the "common" or black wire from the dimmer should connect to the third wire that DID NOT HAVE POWER no matter which position the other switch was in.
The second (and less common) mistake with 3-way systems and dimmers is that certain dimmers are REQUIRED to be on either the power or switchleg side to work properly. If this is required it should be stated in the instructions!. Good luck and feel free to reply if you're still having trouble getting it going.
Posted on Feb 04, 2010
I'm assuming you've connected the line (hot) on the black and the load (out to fixture) to the red? So does the light stay on or your tester is measuring voltage. Some electronic controls will test voltage on a tester. if there is no load connected
Posted on Aug 03, 2010
Tips for a great answer:
Feb 10, 2012 | Leviton MFG L00-IPI06-1LM DIMMER SLIDE...
Mar 05, 2011 | Lightolier 600Watt Preset Slide Dimmer
Feb 22, 2011 | Leviton MFG L00-IPI06-1LM DIMMER SLIDE...
Dec 29, 2010 | Leviton 604-6633PW Decora Slide Dimmer...
Oct 31, 2010 | Leviton #L11-06681-00I Ivory 600 Watt Push...
Oct 16, 2010 | Lutron #DVW-603PGH-WH 600W White Single...
Oct 15, 2010 | Leviton Decora Light Dimmer Switch
Aug 03, 2010 | Leviton MFG L00-IPI06-1LM DIMMER SLIDE...
Mar 17, 2009 | Lutron #D-600PH-DK 600W SP Push Rotating...
Nov 02, 2008 | Leviton Decora Light Dimmer Switch
70 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: