Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Procom ML200TBA
Propane appliances usually run on 10-11 inches of water column, this is about 1/2 pound of pressure. If the regulator you have is not rated for delivering gas at that rate, you will need to find one that does. If your regulator is rated for more than the 11 inches, most likely you could have damaged the appliance regulator that came with the heater. Check the propane pressure specified by the heater manufacture against the rated supply of your regulator and see if they match. Make sure the heater is rated for Propane and NOT Natural Gas. Check to see if the gas valve on the appliance is in the operate position and all valves are open. Bleed off the air in the gas line by holding down the pilot switch and keep attempting to light the pilot. It could take you a few minutes. If you hear and smell gas but the unit will still not light, don't chance at getting hurt, call a technician. Look to make sure there are no safety switch that may have triggered off not allowing the gas valve to operate. And make sure there is no obstruction in the heater?s gas valve blocking off the supply of gas. Always exercise caution when it comes to gas and if you are uncomfortable, call a qualified gas technician.
Posted on Sep 17, 2007
SOURCE: Pilot light goes out!
Have a technician check your gas pressure, your pilot should be nice and blue. You could start by replacing the thermocouple but I think it is gas related.Is there a pilot adjustment screw on the gas valve? If so increase the flame. Has it always done this? If so, is the model made for the specific gas being used i.e. Natural Gas or Propane and it may be operating on the wrong gas? Let me know what you find, Thanks!
Have a technician check your gas pressure, your pilot should be nice and blue. You could start by replacing the thermocouple but I think it is gas related.Is there a pilot adjustment screw on the gas valve? If so increase the flame. Has it always done this? If so, is the model made for the specific gas being used i.e. Natural Gas or Propane and it may be operating on the wrong gas?
Let me know what you find, Thanks!
Posted on Oct 11, 2007
SOURCE: Pilot goes out!!
Just a hunch, but most propane have left handed threads. Meaning they turn the opposite from everything else. Its possible you are turning the gas off by mistake.
Posted on Mar 09, 2008
check the connections with some washing up liquied and water in a bowel and try the connections with this , it should help find your leak use a paint brush to put on
Posted on Jan 13, 2009
the pilot and clean the injector and see if this is clear then try it , you will need a pressure gauge to check the gas pressure ,
Posted on Feb 03, 2010
Tips for a great answer:
Jan 03, 2016 | Procom Heating & Cooling
Jan 29, 2013 | Heating & Cooling
Oct 12, 2012 | Procom ML300TBA Heater
Dec 23, 2010 | Procom ML300EBC Heater
Dec 15, 2010 | Procom QL300TYLA Heater
Oct 09, 2010 | Procom (177653) Utility Heater
Oct 20, 2009 | Procom 10K BTU, Vent Free, 2 Plaque...
Mar 09, 2008 | Procom ML300TBA Heater
79 people viewed this question
Usually answered in minutes!