Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like the fan switch on the furnace is set to low. Turn power off to furnace, take door off of furnace look for a fan switch, it may be a fan - limit together. The limit settings should be approximately 160° to 200°, and the fan settings should be about 100° to 140° set it to 120° it it's already set there then you probably need to replace it.
Posted on Aug 23, 2009
Look at pressure switch and inspect the tubing for any water logging, crimps, or cracks. Also ensure there are no obstructions in the vent line.
Is the ignitor glowing at all? Did you test the voltage going to the ignitor?
I hope you find this information to be very helpful to you moving forward. :-)
Posted on May 10, 2010
SOURCE: we need to change the
Not an easy task! Take many pictures as well as draw out and mark which wire went where. You will have to remove everything from inside the cabinet to get to the heat exchanger. It may be easier to replace the furnace. If you are paying a professional to do the exchange, figure three hours if they have done it before, if not figure 5 to 6.
Posted on Apr 02, 2011
Tips for a great answer:
Oct 12, 2014 | Heating & Cooling
Jan 10, 2013 | Heating & Cooling
Apr 02, 2011 | Goodman Heating & Cooling
Feb 09, 2011 | Goodman Heating & Cooling
Nov 08, 2010 | Goodman GMS90703BXA Heater
May 10, 2010 | Goodman GMS90703BXA Heater
Aug 03, 2009 | Heating & Cooling
Jan 07, 2008 | Goodman GMS90703BXA Heater
28 people viewed this question
Usually answered in minutes!