Question about Electrical Supplies
YOU WILL NEED A 2 POLE @ THE HOME PANEL AND ANOTHER @ THE BARN PLUG THE ONE @ THE HOUSE AS YOU NORMALLY. WOULD PLUG THE ONE @ THE BARN ONTO THE BUSS IN THE MLO PANEL AS IF IT WERE TO BE A FEEDER BUT INSTEAD PUT THE 2 PHASE WIRES ON IT , THIS WAY YOU WILL HAVE A MEANS OF DIS-CONNECT AT THE BARN AS WELL, YOU WILL STILL NEED A GROUND ROD @ THE BARN TO GND THE MLO PANEL AND ALL RECPT SHOULD BE GFCI RATED FOR SAFETY AS FAR AS THE WIRE SIZE DONT KNOW LOAD , BUT A GUESS WOULD BE A # 4 COPPER TRI OR A # 2 ALUM SHOULD HANDLE WHAT YOUR GOING TO DO , JUST A GUESS .
Posted on Nov 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 15, 2014 | NetGear WGR614 Wireless Router
Dec 06, 2012 | Bosch PowerStar AE125 AE125 Whole House...
Sep 26, 2012 | Square D Qo 200 Amp 40 Circuit Indoor...
Jan 04, 2012 | Siemens 100 Amp Main Breaker Renovation...
Oct 03, 2010 | Siemens 100 Amp Main Breaker Renovation...
May 13, 2009 | Electrical Supplies
Dec 17, 2008 | Pacific International Federal Pacific...
Jan 19, 2017 | Electrical Supplies
380 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: