Question about Goodman CLQ36AR49 Air Conditioner
(New goodman 3 ton gas package unit) I Replaced the board in the unit, I have the same problem with the new board as I did with the original board, the unit will not stop running.I unplugged the thermostat wires in the unit and wire caped I then plugged in the disconnect. The unit starts right up in adition to that my led light is blank I cant see having two bad boards any sugestions
What is keep running?
Posted on Nov 30, 2013
Does that unit run heating or just the fan run? if just the fan you may have a bad fan thermostat
Posted on Oct 21, 2008
Tips for a great answer:
"PLACE A JUMPER (PIECE OF WIRE) BETWEEN Y AND W IF YOU ARE USING A HEAT PUMP WITHOUT AUXILIARY/BACKUP HEAT." if this dosnt work check the fuse in the air handler you may have blown it if you did not turn the unit off before installing.
Mar 25, 2014 | Goodman Air Conditioners
Apr 02, 2013 | Goodman Manufacturing GPH1336H21A -...
Jan 23, 2013 | Goodman Manufacturing GPG1342090M41...
Aug 17, 2012 | Goodman Air Conditioners
Aug 02, 2010 | Goodman Air Conditioners
Jan 29, 2009 | Air Conditioners
Jan 21, 2008 | Bryant 462AJC021BA Air Conditioner
112 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: