Question about Ruud Heating & Cooling
Inside your furnace their are two probes one is inthe shape of a paper clip the other is a straight probe this one needs to be taken out and cleaned using emery cloth be sure not to touch this probe after cleaning or you will have to replace
Posted on Oct 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 22, 2013 | Goodman GMS90703BXA Heater
Feb 12, 2013 | Heating & Cooling
Jan 25, 2013 | Heating & Cooling
Jan 15, 2013 | Heating & Cooling
Feb 15, 2011 | Goodman GMS90703BXA Heater
1. Thermostat calls for heat. 2. Draft inducer motor starts. 3. Pressure switch attached by a small plastic or rubber tube senses the negative pressure produced by the draft inducer and closes. 4. Draft inducer runs for 30 seconds to a minute before you hear a gas hissing sound. The ignitor did not glow, the flame sensor (a small metal probe about 1/8" in diameter, with a white porcelain base) does not sense the flame, so after 8 to 10 seconds the hissing sounds stops with no ignition of gas to heat your home. Your furnace shuts down and goes into a lock out condition until you turn your power switch back off and on again. Then the sequence starts all over again with no ignition of the gas. Solution: You probably need to purchase and install a new ignitor. I would suggest that you inspect your ignitor closely for cracks. Make sure you do not touch the ignitor with your bare hands. If you do not visually see a crack, then you could have a furnace control board problem or a limit, rollout switch problem. The furnace's control board might not be supplying the voltage to the ignitor. If your furnace lights and the gas stays on for 8 to 10 seconds, then shuts right back off, then you need to clean your flame sensor with light sand paper or steel wool. You might need a new flame sensor, but most of the time they can be cleaned an will work well after cleaning.
Nov 26, 2010 | Heating & Cooling
Mar 30, 2010 | York Furnace Draft Inducer Blower Fasco #...
Dec 08, 2009 | York Furnace Draft Inducer Blower Fasco #...
Nov 22, 2008 | Heating & Cooling
73 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: