Question about LG Heating & Cooling
I can figure out what model a/c you have from this discription/ is this a lg floor mod. or window model or lg duckless split system
one comon problem causing faut is dirty filter or condensor but hard to figure if i cant place the unit disciption.
Posted on Oct 20, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 05, 2015 | Heating & Cooling
May 12, 2014 | LG Heating & Cooling
Feb 23, 2011 | LG Heating & Cooling
Feb 03, 2011 | LG LA185HV Split System Air Conditioner
Jan 24, 2011 | LG Heating & Cooling
Jul 14, 2009 | LG Heating & Cooling
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
6 - DC Peak Error
• Supplied power is not normal
• Comp Connector (CN-U,V,W) is disconnected or inserted to wrong
• Compressor is damaged (coil short) ? replace compressor
• Too much Refrigerant
• Defect in outdoor pcb assembly ? replace pcb assembly
Try turning power off to external unit, usually resets diagnostics and runs OK. If not PCB external unit likely culprit, replace!
Jul 31, 2008 | Heating & Cooling
Feb 12, 2008 | Heating & Cooling
335 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: