Question about Intertherm P3RA-048K Air Conditioner
The blower is smoking because you have it hooked up to the same wires you've hooked the electric coil to. That coil runs on 240 volts. Those wires are typically red and black. The motor runs on 120. One of the wires should be shifted to a neutral (white wire). Assuming the motor is still alive...this will fix it.
Posted on Nov 23, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 26, 2015 | Goodman Heating & Cooling
Jan 04, 2014 | Intertherm Heating & Cooling
Jul 15, 2011 | Intertherm Heating & Cooling
Dec 19, 2010 | Intertherm P3RA-036K Air Conditioner
Jun 05, 2010 | Intertherm P3RA-048K Air Conditioner
Oct 23, 2009 | Heating & Cooling
Aug 31, 2009 | Heating & Cooling
Apr 07, 2009 | Intertherm P3RA-030K Air Conditioner
Oct 19, 2008 | Intertherm P3RA-048K Air Conditioner
Oct 12, 2007 | Intertherm P3RA-048K Air Conditioner
100 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: