Question about Heating & Cooling
Your best bet and where i would start is to identify where the coulors are conected at the fernace. in the industry we use standard wireing coulors wher green is g for fan and red is rh=switched trans power for heating . rc=switched transformer power for cooling . now normaly there is only one transormer so you would put a jumper from rc to rh and conect the red wire from the furnace to eather of these.jumper installed. the y is your cooling witch is normaly the yellow wire. o on the stat is for a heat pump if you nead to energize reversing valve in cooling mode . w is first stage heating and this can be conected to eather brown or white youll have to check at the furnace to see witch it is . the final wire eather brown or white should be conected to c or 24v common witch you didnt say you see on the thermostat. once again
red to rc and rh
green to g
yellow to y
brown or white to w
brown or white to common or c
please post feadback hope i was of help
Posted on Oct 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 01, 2015 | Ruud Central System Air Conditioner
Jun 07, 2014 | Hunter 30124 Air Conditioner
Dec 29, 2010 | Heating & Cooling
Jan 14, 2010 | Heating & Cooling
Oct 04, 2009 | Heating & Cooling
Aug 22, 2009 | Hunter 30124 Air Conditioner
613 people viewed this question
Usually answered in minutes!