Question about Carrier Heating & Cooling
Check the side of outdoor unit for a name plate and see if breaker is correct size as is required on name plate. then test, run and start capacitor to see if within 10 percent of rated value. if ok then look at contactor to see if you are starving voltage through it to compressor. if you are then back trace to main electrical panel and see if breaker that feeds outside disconnect is good and wires are snug. then check breakers adjacent to it to see if they are good and transferring heat improperly.
Posted on Oct 19, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 21, 2015 | Dryers
Feb 20, 2015 | Heating & Cooling
Aug 10, 2011 | Whirlpool Heating & Cooling
Dec 28, 2010 | Carrier 38CKC036 Air Conditioner
Aug 06, 2010 | Heating & Cooling
Jun 15, 2010 | Dometic Rooftop RV Air Conditioner
Jun 30, 2009 | Dometic Rooftop RV Air Conditioner
Sep 03, 2007 | Heating & Cooling
81 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: