Question about Ruud Heating & Cooling
Repost with more specific . motor aka fan is running?stat is set to heat and max heat? how old? general progression is as follows. stat says its cold. signal is sent to gas valve to open. gas valve looks to see if pilot is lit via thermocouple. if pilot is lit then main valve opens and burner lights. shortly thereafter sufficient heat builds up to trip heat sensor that turns on fan and blows hot air into house.many times a tripped safty causes a default fan response. aka when you show up the fan is on 24 7 . that equals a failed safety and needs a pro tech to see why saftyfailed.
Posted on Oct 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 13, 2013 | Heating & Cooling
Nov 03, 2013 | Ruud Heating & Cooling
May 14, 2011 | Ruud Heating & Cooling
May 10, 2011 | Heating & Cooling
Nov 30, 2010 | Ruud Heating & Cooling
Nov 06, 2010 | Ruud UAPA024 Air Conditioner
Mar 07, 2010 | Ruud UBHC Air Conditioner
Oct 06, 2009 | Ruud Heating & Cooling
Jun 24, 2009 | Ruud Central System Air Conditioner
Sep 15, 2008 | Ruud UBHC Air Conditioner
411 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: