Question about Goodman Air Conditioners
I'm not familiar with that model # but most furnaces are similar. R goes to R (usually the red wire). If you don't have a seperate heat source, like a boiler, the wire needs to connect to both Rc & Rh. Stats usually come with a jumper in place. Then W to W (usually white), G to G (usually green) and Y to Y (usually yellow or blue). Before you make any connections, TURN OFF YOUR FURNACE. If you don't, you'll probably blow the fuse on the control board, or worse yet, blow your transformer.
Posted on Oct 16, 2008
Tips for a great answer:
Jan 07, 2015 | Hunter Air Conditioners
Sep 15, 2014 | Hunter Set and Save Programmable...
Sep 12, 2014 | Hunter Set and Save Programmable...
Aug 24, 2013 | Air Conditioners
Oct 04, 2009 | Air Conditioners
Jun 30, 2009 | Air Conditioners
107 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: