Question about Amana Heating & Cooling
This sounds like your condenser contactor, contacts are stuck. They weld together if an ant or other debree get between the contacts. Turn off the electric breaker to the outdoor unit as if the outdoor unit runs without the indoor unit running you may damage your outdoor unit compressor.
I would suggest you call a service company. The part should run retail @ 30 to 40 dollars then the service call charge. This repair should take less than 1/2 hour.
Posted on Oct 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 22, 2012 | Frigidaire FRA186MT2 Window Air...
Feb 13, 2012 | Heating & Cooling
Aug 20, 2010 | Amana Heating & Cooling
Jun 26, 2010 | Amana Comfort Zone 12M32PBEH Air...
Jun 25, 2009 | Heating & Cooling
May 03, 2009 | Carrier Heating & Cooling
Aug 05, 2008 | Heating & Cooling
Jan 17, 2017 | Amana Heating & Cooling
409 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: