Question about Protech Systems FasNSeal FSWMKE4 4" Vent Kit for Wall Mounted Boilers & Wat
Hot water is ok but the c/h wont come on
The pump default light is on and it won't heat the floor or the tap water but you can hear the pump running. I checked the incoming filter or screen and on the right hand side of the pump there is a yellow handled valve for a little drain. While the pump is running I opened the valve and nothing comes out. Is the pump shot or what can I try next.
Posted on Jan 25, 2009
Diaphragm is punctured in 3 way valve. replace small one on top of valve. about 7 pounds from plumbing supply centre. Diaphragm on DHW side ok if water still running hot. I would however replace both, as if one has filed the other maybe about due for a change also.
Posted on Jan 10, 2009
The diaphragm has a hole in it. This is the small one on top of the 3 way valve. If you have Hot water the larger diaphragm at the front of the valve will be ok. The diaphragms are in the cases behind the micro switches (On the Brass unit on LH side is you look into the boiler) . You need to close taps under boiler and drain primary circuit, and the when pressure gauge at zero you can remove the thin metal sensing pipes that are located into the 3 way valve. The parts will cost approx 8 pounds each from somewhere like PTS (check Google - Plumbing trade Supplies) Regards
Posted on Jan 08, 2009
Baxi boiler relief valve blows off when heat is turned on when hot water is working it is fine
Posted on Nov 02, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 28, 2013 | Water Heaters
Jan 23, 2011 | Water Heaters
Oct 12, 2009 | Water Heaters
Mar 23, 2009 | Water Heaters
Dec 30, 2008 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Nov 17, 2008 | Water Heaters
666 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: