Question about Frigidaire Heating & Cooling
We just had the same problem. Try going outside, find the air intake and see if it's full of snow! We just did that and voila, the furnace roared to life!!
Posted on Dec 21, 2008
There is a pressure switch on the inducer motor with a rubber hose attached to it. Make sure that this hose is attached and is not cut or leaking, it's much like a vacuum hose on a car. Also make sure that the inducer motor is operating normally, nothing blocking the flow of air through the flue.
Posted on Oct 15, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 23, 2016 | Heating & Cooling
Nov 21, 2015 | Heating & Cooling
Oct 28, 2011 | Goodman Heating & Cooling
Oct 18, 2011 | Goodman GMS90703BXA Heater
Feb 03, 2011 | Goodman Heating & Cooling
Dec 10, 2010 | Goodman GMS80903BNA Heater
Dec 02, 2010 | Heating & Cooling
Dec 12, 2009 | Heating & Cooling
Apr 13, 2009 | Heating & Cooling
Nov 23, 2008 | Goodman GMS90703BXA Heater
Dec 20, 2016 | Frigidaire Heating & Cooling
370 people viewed this question
Usually answered in minutes!