My Goodman GSC130361DE 60 Htz has problem with coils iceing up. Cleaned several times.
Hi, I am assuming you are talking about the indoor coil icing up when you are in cooling. The reason I am asking this as this appears to be a heat-pump and they will ice up in the winter at the outdoor unit. I will go with the indoor coil. If the indoor fan is blowing up to speed and you have cleaned the indoor coil but still have this ice forming, it could very well be that you are low on freon. This will also cause the suction line, the large copper line outdoors to ice and on into the indoor coil. This will happen if you have developed a leak some where. Also, make sure you have good strong return air coming back through the air filter, because if you have problems with the duct work like holes from varments, or you have had any repairman around the duct work, sometimes they will flatten it causing no air flow and you will have ice. My bet is you are low on gas. Shut the unit off to make sure it has no ice on the coil, and go to the outdoor unit. Have someone turn it to cooling and put your hand above the fan on the condenser coil. The air should start to get warm and then hot if the freon level is ok. This also depends on the outdoor temperatures. The hotter it is outdoors, the hotter the air will be. If it is rather cool, around lets say 75*F, and this copper suction line is starting to form ice, the problem is it is low on freon. In this case, this is something you will need to call a tech out to charge the unit. You have to be certified and be able to buy the right freon which is only available to a/c and refrigeration tech's. If this is a heat -pump, and it is winter where you are and the outdoor coil is icing up, let me know and I can go through the steps to check this out. I do believe this is a summer problem where you may be, but you never know unless you ask. Please don't forget to rate me on this post as I am sure you will be kind. I wish I could save you a tech call, but if its low and you have cleaned the indoor coils, and filter is clean, then this is the problem.
A/C, Heating, & Refrigeration Contractor
Sep 26, 2010 |
Goodman CLQ36AR49 Air Conditioner