Question about Pipes, Fittings & Valves
We have a water well and for some reason the pressure is low coming out of the showers. If we run two sinks at a time they become slow too. We just had a new well pump installed. I read something about seeing if the filter is clogged. Where is this filter located? Is it in the well itself? We just changed the house filter so i know that is not the problem. Help!
Take a regular tire presssure guagge and go to where you bladder tank is and there should be a removable cap that you can remove and then check the pressure that you have in the tank. If you only get water out then the blader is gone. if there is no pressure then you will have to charge it up. recommend aroud 60 psi and the reinstall the cap. also the filter that they are talking about is probably a strainer and it should be in the line before the pump. Good Luck
Posted on Dec 24, 2008
There is usually a metal filter at the wellpoint on the bottom of your drop-tube, but I don't think that is the problem if you are not getting particles in your water. This is easy to check for just by putting water in a glass and looking for little specks.
I would be more inclined to look for holes in the drop-tube where AIR is getting into the system, thus reducing the suction of the pump.
If you are using a "bladder tank" to maintain pressure, it could be that the "off" setting is too low. You want that to be in the 50-60 psi area. "ON" should be about 40 psi.
Anyway, I think an air leak is the more likely problem, but to find out for sure, you almost have to pull the drop-tube, which might be very long. That would best be left to a well service company.
Posted on Oct 10, 2008
Tips for a great answer:
May 24, 2014 | Pipes, Fittings & Valves
Sep 10, 2013 | Latoscana TC3TPW690 Water Harmony...
Apr 01, 2013 | Delta Faucet Delta RP17453 Pull-Down...
Nov 14, 2012 | Pipes, Fittings & Valves
May 19, 2011 | Pipes, Fittings & Valves
Jun 02, 2010 | Pipes, Fittings & Valves
Nov 08, 2009 | Delta RP17453SS Standard Diverter Tub...
Jun 27, 2009 | Brasstech ''P'' Trap Kit - 3013
Mar 06, 2009 | Pipes, Fittings & Valves
481 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: