Question about Goodman GDS80703ANA Open Flame Mid-Size Heater
I replaced the pressure switch last week and the new one did the same thing. Then I discovered the cause by accident. With the breaker shut off I was poking around the wiring looking for loose connections. I noticed that the wiring harness plugged into the control board was not supported in any way. I have considerable electrical/electronics experience and one thing I know is that you never hang anything from plugs or connectors. Playing my hunch I tied off the harness so it wasn't hanging from the plug any more and now the furnace works normally. Apparently the weight of the harness hanging from the connector has damaged its connections on the control board. I'll probably have to replace it eventually but for now the problem is solved. I suspect this poor design feature may be connected with Goodman furnaces being notorious for control board failures.
Posted on Nov 30, 2008
Go ahead and change, or have changed the pressure switch. they're not too terribly expensive and they are real easy to put in. we have them in stock and can ship it out on monday. we'll need the full model number of your unit to make sure to get the correct one priced for you. you can send a request to our office via our parts website at: http://hstrial-cseagraves1.intuitwebsites.com/hvacpartsnet.html
Posted on Nov 30, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 08, 2017 | Heating & Cooling
Jan 06, 2017 | Heating & Cooling
Jan 03, 2017 | Coleman Heating & Cooling
Jan 03, 2017 | Heating & Cooling
Jan 08, 2016 | Comfort Zone CZ1500WC Infra-Red...
Dec 12, 2010 | Stoves Heating & Cooling
Dec 21, 2013 | Goodman GDS80703ANA Open Flame Mid-Size...
Jan 29, 2012 | Goodman GDS80703ANA Open Flame Mid-Size...
305 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: